1.1 These requirements cover industrial control panels intended for general industrial use, operating from a voltage of 600 volts or less. This equipment is intended for installation in ordinary locations, in accordance with the National Electrical Code, ANSI/NFPA 70, where the ambient temperature does not exceed 40°C (104°F) maximum.
1.1 revised effective April 25, 2003
1.2 These requirements also cover industrial control panel enclosures and industrial control panels intended for flame safety supervision of combustible fuel type equipment, elevator control, crane or hoist control, service equipment use, marine use, air conditioning and refrigeration equipment, and for control of industrial machinery including metalworking machine tools, power press controls, and plastic injection molding machinery.
1.2 revised effective April 25, 2003
1.3 This equipment consists of assemblies of two or more power circuit components, such as motor controllers, overload relays, fused disconnect switches, and circuit breakers, or control circuit components, such as pushbuttons, pilot lights, selector switches, timers, and control relays, or a combination of power and control circuit components, with associated wiring, and terminals . These components are mounted on, or contained within, an enclosure, or are mounted on a sub-panel.
1.3 revised September 1, 2005
1.3.1 An industrial control panel does not include an evaluation of the controlled equipment such as motors, heaters, lighting, and other loads connected to power circuits. Unless specifically noted on the wiring diagram of the industrial control panel, an industrial control panel does not include equipment mounted remotely from the panel and connected via a wiring systems or equipment field installed on or within the industrial control panel.
1.3.1 added September 1, 2005
1.3.2 An evaluation of the adequacy of the controls and protective devices contained in an industrial control panel for supervision and proper functioning of the controlled loads or equipment is not covered by the requirements in this standard. Such evaluations are covered by the standards applicable to the complete piece of utilization equipment.
1.3.2 added September 1, 2005
1.3.3 The evaluation of a pre-fabricated building, structure, or platforms supplied with industrial control panels are not covered by the requirements in this standard.
1.3.3 added September 1, 2005
1.4 Fire pump controllers are covered by the Standard for Fire Pump Controllers, UL 218.
1.4 revised effective April 25, 2003
1.5 Equipment intended for use in hazardous locations, as defined in the National Electrical Code, ANSI/NFPA 70, are covered by the Standard for Industrial Control Equipment for Use in Hazardous (Classified) Locations, UL 698.
1.5 revised effective April 25, 2003
1.6 Industrial control panels incorporating intrinsic safety barriers and intended for connection to circuits residing in hazardous locations are covered by the Standard for Industrial Control Panels Relating to Hazardous (Classified) Locations, UL 698A.
1.6 revised effective April 25, 2003
1.6.1 Motor control centers, including motor control center sections and units, or equipment intended for field installation into a motor control center are covered by the Standard for Motor Control Centers, UL 845.
1.6.1 added September 1, 2005
1.6.2 Assemblies of electrical control units or equipment containing electrical control units for fire-protective signaling systems are covered by the Standard for Control Units and Accessories for Fire Alarm Systems, UL 864.
1.6.2 revised December 28, 2007
1.6.3 A freestanding assembly of circuit breakers and busses for control of electric light and power circuits or equipment intended for field installation in dead-front switchboards are covered by the Standard for Switchboards, UL 891.
1.6.3 revised December 28, 2007
1.6.4 Equipment intended to supply automatic illumination, power, or both, to critical areas and equipment essential to safety of human life is covered by the Standard for Emergency Lighting and Power Equipment, UL 924.
1.6.4 added September 1, 2005
1.6.5 Deleted, effective date to be determined
1.6.6 Control equipment for use with swimming pools and spas is covered by the Standard for Electric Spas, Equipment Assemblies, and Associated Equipment, UL 1563.
1.6.6 added September 1, 2005
1.6.7 Portable control panels containing switches, overcurrent protection, and cord connected via attachment plugs and receptacles for use at carnivals, circuses, fairs, exhibition halls, motion picture and television studios, theaters, construction sites and similar locations are covered by the Standard for Portable Power-Distribution Equipment, UL 1640.
1.6.7 added September 1, 2005
1.6.8 Equipment for the control of fuel cells, photovoltaic systems, or utility interactive systems are covered by the Standard for Inverters, Converters, Controllers and Interconnection System Equipment for Use With Distributed Energy Resources, UL 1741.
1.6.8 revised December 28, 2007
1.6.9 Enclosures or pedestals containing terminals for connection of power circuit conductors are covered by the Standard for Termination Boxes, UL 1773.
1.6.9 added September 1, 2005
1.6.10 Emergency alarm equipment or control panels containing emergency alarm equipment are covered by the Standard for General-Purpose Signaling Devices and Systems, UL 2017.
1.6.10 added September 1, 2005
1.6.11 Equipment for gas or vapor detection or control panels containing gas or vapor detection equipment is covered by the Standard for Gas and Vapor Detectors and Sensors, UL 2075.
1.6.11 added September 1, 2005
1.6.12 Control panels containing predominately communication equipment, such as telephone equipment and intended for installation in accordance with Chapter 8 of the NEC, is evaluated to the Standard for Information Technology Equipment, UL 60950.
1.6.12 added September 1, 2005
1.6.13 Control equipment intended for use in physical access control systems, which provide an attended or unattended means of monitoring or controlling traffic through portals of a protected area for security purposes; or in key management systems, which regulate or control access to the use of a device by electrical, electronic or mechanical means, are covered by the Standard for Access Control System Units, UL 294.
1.6.13 added December 28, 2007
1.6.14 Electrically operated or mechanically operated control equipment or enclosures intended for theft deterrent or warning purposes, such as detectors, security containers or alarms for merchandise or property, are covered by the Standard for Antitheft Alarms and Devices, UL 1037.
1.6.14 added December 28, 2007
1.7 Deleted September 1, 2005
Copyright © 2018 | MH Corporate basic by MH Themes